IBEW Loses Sister Katharina (Kat) Engnell
The IBEW loses Sister Katharina (Kat) Engnell, a licensed journeyman electrician from Local 46 in Seattle, Washington. Engell was electrocuted and died on the job on November 20, 2008 at the Saint Gobain glass plant.
Kat Engnell was an amazing woman. Originally from the South, Kat moved to Seattle after receiving her Masters Degree in Fine Arts. She bought a beautiful home in Seattle’s Columbia City neighborhood and then decided to become an electrician. She started attending the PSEJATC Apprenticeship program in 2000.
Kat was a most humble, hard working, serious electrician. Diversity and full inclusion in the electrical industry were passions of hers. The fact that a scholarship for those seeking to become Union Trades people is being funded in her name testifies to that. If you would like to donate, please make checks or money orders payable to the Katharina Engnell Memorial Schollarship Fund, Account 471001014441 at Key Bank.
Her interests included kayaking, raising hens, collecting antiques, creating and teaching art, politics, unionism, and rocking out to hippy music. If there was a party, Kat was there having a good time. She was a fantastic mechanic, intellectual, and a bohemian all in one. All who knew her can say that her kindness and generosity were boundless. She will be missed but will live on in the memories and stories of her, and in the kindness and care we show to each other in this truly dangerous field.
There is a memorial at the job site and a memorial service will be held at the IBEW Local 46 Hall in Kent, Washington on Thursday, December 4, 2008 at 5:00 p.m.
For me, the loss of any worker on the job is tragic. But the loss of an electrician is personal.
My personal condolences to Kat’s friends and family. My thanks to Nicole Grant for this information.
IBEW Local 48
Update: The following info was taken from IBEW Local 46 website.
This item was posted on the IBEW Local 46 web site
IBEW Local 46 Electrician, Kat Engnell, was killed at work, Thursday,
November 20, 2008, during the day shift at the Saint Gobain glass plant. Kat
was up on a metal platform, like a catwalk, doing lighting maintenance. It
is normal to work on equipment up there while it is still ‘hot’,
unfortunately, while Kat was changing out a 500W 120V fixture, after making
sure that the ground and neutrals had both been made up, she was
electrocuted and died. She was found by a Local 46 Brother working on sight
who stayed with her body until the fire crew got her down and took her away.
The following comment was left via email by a Safety professional:
I suspect that she was not wearing rubber insulating gloves, considered by
most electricians as unnecessary and too cumbersome for this type of low
According to 1910 subpart S
1910.333(a)(1) “Live parts to which an employee may be exposed shall be
deenergized before the employee works on or near them….” (does not apply to
circuits of 50 volts or less)
1910.333(a)(2) “If the exposed live parts are not deenergized (i.e., for
reasons of increased or additional hazards or infeasability) other
safety-related work practices shall be employed …”
1910.335(a)(1)(i) Employees working in areas where there are potential
electrical hazards shall be provided with, and shall use, electrical
protective equipment that is appropriate for the specific parts of the body
to be protected and for the work to be performed.
NFPA 70E 2009 – Table 130.7(C)(9)
Panelboards or other equipment rated 240 volts and below
Work on energized electrical conductors or circuit parts, including voltage
testing requires the use of Rubber Insulating gloves and Insulated or